What's wrong with this picture?
If you said the chimney is missing a chimney cap, you're right! Such a simple, inexpensive fix. However, if this is left like this, you could be facing one or more of the following issues:
1. Chimney caps keep out birds, BATS, squirrels, and other small rodents. If something crawls into your chimney but gets stuck and can't get out (which happens a lot), not only is that awful for the animal, but you will also be dealing with a dead critter, bad smells, and even bugs (maggots, etc.). Yuck.
2. SAFETY ISSUE - wood burning fireplaces sometimes emit large burning embers that float up the chimney and without a cap, can land on your roof or something equally flammable.
3. Chimney caps help reduce water/moisture that can damage your chimney liner and other components and can also lead to mold.
4. A correctly placed cap can help block downdrafts and excessive wind (especially during hurricanes and other serious weather events) from channeling down your chimney and blowing smoke and/or soot into your living space. Caps also prevent debris like leaves and small branches/twigs from getting inside your chimney.
So what does all of this mean? If you're buying a house, make sure it has a chimney cap! If you own a house with a chimney, go take a look and make sure you have one and that it is securely placed. If you can't tell, then it's time for a roof inspection.
IF YOUR HOME WAS BUILT IN THE 1960s-80s, CHECK TO SEE IF YOUR HOME HAS THIS ELECTRICAL PANEL: Federal Pacific(FPE)/STAB-Lok electrical panels are panels that have been the subject of UL (Underwriters Laboratories) and consumer concerns related to inadequate safety protection. Consistent evidence has been presented that STAB-LOK breakers have a tendency to become loose and experience failure of unit circuit protection. The breakers often do not trip in the event of an emergency leaving the circuit unprotected - this is a SIGNIFICANT FIRE HAZARD. In addition, this particular home that I recently inspected had frayed rag insulation (see red circle), adding another safety hazard to this situation. Click this link for further information about these panels and the dangers they pose: https://www.washingtonpost.com/lifestyle/home/despite-previous-safety-concerns-this-circuit-breaker-is-still-in-homes/2018/05/08/8927af86-4ef9-11e8-b725-92c89fe3ca4c_story.html?utm_term=.5e452ed7097f
They say a picture is worth a thousand words and sometimes, a video is worth a thousand pictures. In this case, we see a brick support pier that looks a little askew at first glance. But as the video shows, it has completely separated from the wall which can jeopardize the stability of the structure. We use short videos like this when necessary to highlight concerns in a very direct and easy-to-see way. These videos go directly into our web-based home inspection reporting software so that when you receive your report, you are not only getting pictures and detailed language, but also videos when pertinent.
From Rick & Lori:
Yes, we've joined the 21st Century and started a (mini) blog! Check here for great updates and tips about your current or prospective home.