IF YOUR HOME WAS BUILT IN THE 1960s-80s, CHECK TO SEE IF YOUR HOME HAS THIS ELECTRICAL PANEL: Federal Pacific(FPE)/STAB-Lok electrical panels are panels that have been the subject of UL (Underwriters Laboratories) and consumer concerns related to inadequate safety protection. Consistent evidence has been presented that STAB-LOK breakers have a tendency to become loose and experience failure of unit circuit protection. The breakers often do not trip in the event of an emergency leaving the circuit unprotected - this is a SIGNIFICANT FIRE HAZARD. In addition, this particular home that I recently inspected had frayed rag insulation (see red circle), adding another safety hazard to this situation. Click this link for further information about these panels and the dangers they pose: https://www.washingtonpost.com/lifestyle/home/despite-previous-safety-concerns-this-circuit-breaker-is-still-in-homes/2018/05/08/8927af86-4ef9-11e8-b725-92c89fe3ca4c_story.html?utm_term=.5e452ed7097f
Thinking about buying a home? Join us this Saturday, March 9 in Chapel Hill! It’s free and packed full of excellent information and opportunities to ask questions. Our very own home inspector, Rick Doherty, will be on hand to explain the home inspection process and share tips on what to look for when searching for your perfect home. See you there!
Did you know that you should clean your dryer exhaust vent at least once a year (and even more often in larger households)? Nearly 15,000 fires a year are caused by dryer-related fires so this safety maintenance is VERY important. You can hire a professional or you can purchase a kit at a hardware store and do it yourself. In this video, the lint is being blown from inside out as well as using the lint brush connected to a power drill. A clean vent is not only far safer but will also save you time and money as your clothes will dry faster. Win win!
We've got you covered, even if your prospective home's outlets aren't. Missing outlet covers are easy to miss when they are hidden behind furniture and other household items. Without these covers, electrical wires can be exposed presenting hazardous conditions especially to children and pets. Outlet covers are designed to protect you from electrical shock and fire hazards and are something we look for at each home inspection. It is shocking (pun intended) how many homes we see with this easily-fixed issue. We'll put it in your inspection report to alert you of this commonly occurring safety issue.
Can you spot the difference? It's a bit hard to tell to the untrained eye. The top right breaker in the electrical panel has been added or replaced. The new breaker is a different brand from the panel enclosure and is not listed on the label of the inside panel (not viewable here). Breakers must be UL listed and certified for each panel to ensure proper operation. The compatibility of the breaker to the panel needs further evaluation by a licensed electrical contractor to ensure safe and proper operation of the overcurrent protection systems. This is extremely important because without proper compatibility, the top breaker might not trip if overloaded which can lead to overheating and possibly cause a fire. These electrical panels are one of the many systems that gets checked during a home inspection.
From Rick & Lori:
Yes, we've joined the 21st Century and started a (mini) blog! Check here for great updates and tips about your current or prospective home.